Rosedale KS Residential HVAC & Plumbing Services
LBA ServicesRated 4.8 out of 6121 reviews
LBA Services has proudly served the homeowners in Rosedale, KS and the surrounding areas since 1985! Our professional team of local experts is happy to tackle your heating, AC and plumbing problems. From simple maintenance to full replacements, we can help.
We invite you to read some of our reviews below and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Rosedale, KS.
for Rosedale, KS
Our Reviews by City
All 6 Carrier units had low temperature splits. This is due to the location of the units and the dirty nature of the environment. They will require a deep cleaning using a portable sprayer as well as chemical condenser cleaner. Customer will need to move items on pallets near the units to prevent water damage.
Cleaned out all condenser coils of all Carrier Units. Verified all Carrier Units are cooling at this time.
I recommend replacing the (2) compressor contactors for units 3 and 4 SN: 1608G20183, and 1608G2018. They are both worn and pitted. This quote includes all parts and labor required to replace the 2 contactors. This quote is valid for 30 days. 08/30/2021 Installed new compressor contactors on both units, after contactors been replaced I checked operation of cooling mode at this time everything is working ok
Performed full cooling maintenance. We checked mechanical and electrical components. Changed filters and performed a basic condenser cleaning. We also checked temperature splits. Temperature splits are out of the proper range. Units will require a deep cleaning with water and chemical. Quotes have been sent for repairs
Assisted kellan with scheduled maintenance.
Drain clean out that customer wants replaced is to close to very large and very heavy equipment. We will only dig if equipment is moved. It is to dangerous to excavate this close to that much weight. Ink has dried and turned into a rubber substance tat cannot be removed with jetting or cabling.
Upon arrival 3â€ cleanout for floor drain line was holding water. Attempted to auger line but hit a significant blockage 5â€™ in. LBA tech had the same issue on the previous visit. Each floor drain held water at different levels so attempts were made to clear them. Itâ€™s determined that line is full of ink sludge. Water and plunging moved the blockage down the line, but drains still hold water. Recommend repairing of cleanout line so that a sewer machine or jetter can properly clear the line.
Estimate for adding drain in floor
I preformed a scheduled maintenance and safety inspection on six package units for heating operation. All systems are operating properly and within factory specifications at this time and all filters have been changed.