Lake Waukomis MO Residential HVAC & Plumbing Services
LBA Air Conditioning, Heating & PlumbingRated 4.8 out of 6704 reviews
Whether you’re just starting or ending your day…or somewhere in between…you can count on things going a little smoother with LBA Services as your home comfort partners. We have been providing air conditioning, heating, water heater and plumbing services to the residents of Lake Waukomis, MO and the surrounding areas since 1985!
We provide a full range of maintenance, repair and installation services here in Lake Waukomis, MO and throughout the Kansas City area. From routine tune-ups to 24/7 emergency repairs – when our Heroes really get to shine – we have you covered to help keep your home comfort systems in top working order. Read our reviews below to learn more about us and our exceptional customer service near you!
for Lake Waukomis, MO
Our Reviews by City
Caleb - Lake Waukomis, MO 64151
Corbin checked everything and replaced a part. Then after he left, called his supervisor to ask his thoughts on the issue before returning and fixing something else.
Lisa - Lake Waukomis, MO 64151
Jesus and Jacob were prompt and professional. Jesus did an amazing job of explaining the processes and workings of the units. He provided information about how to keep the units working efficiently.
Great Service! Very timely!
Joe - Lake Waukomis, MO 64151
The technician was straight forward and made recommendations. He did not try to oversell his sales pitch. That usually turns me away from a company when they do that.
Joyce - Lake Waukomis, MO 64151
Arrived to call for Ecobee thermostat stating the house temperature had risen three degrees even though the call for cooling had never stopped. Upon arrival I starting performing my inspection at the outdoor condenser. The compressor was pulling correct amperage and the refrigerant temps/pressures showed a unit charged within spec. The fan however was pulling less than spec amps and the duel run capacitor had lost capacitance on the fan side. It was performing at 3.5 mfd when spec is 4.7-5.3. With customers approval I replaced this. On the indoor unit I found a dirty air filter that I recommended replacing more often to allow better airflow over the indoor coil. The temp split over the coil performed within spec. I then checked blower operation with it pulling correct amperage and the capacitor that feeds it operating within spec as well. If this issue continues while the AC is running this is an insulation issue rather than an AC not operating properly issue. AC running upon departure