Platte City MO Residential HVAC & Plumbing Services
LBA ServicesRated 4.8 out of 6115 reviews
Your home is your oasis…your own private sanctuary. A place where you can relax knowing that, even if a problem occurs with your plumbing, heating, or air conditioning systems, one quick call to LBA Services will take care of everything. At LBA Air Conditioning, Heating and Plumbing, we work hard, 24/7 if necessary, to give homeowners in Platte City, MO that peace of mind.
Please check out a few of our reviews below to find out why your neighbors consider us to be their go-to heating and air company and local plumber in Platte City, MO.
for Platte City, MO
Our Reviews by City
Main sewer line problems
Jim - Platte City, MO
Great Service, so Friendly~~~
Hillcrest - Platte City, MO
Jim - Platte City, MO
Carly did a great job. He explained everything very well and was very courteous.
Baker - Platte City, MO
Ellen - Platte City, MO
New Garbage Disposal
Tim - Platte City, MO
Great service! Called late on Friday and they had a new disposal by noon on Saturday. I will be calling again!
Pat - Platte City, MO
Ellen B - Platte City, MO
The technician was really nice and took the time to explain any findings and suggestions.
Upon arrival I found that the capacitor has failed. I contacted Scott McKinley for pricing and gave customer estimates. Gave customer friends and family discount and he agreed to have system fixed. After repairs were made the system was testing as it should at this time
Completed full heating maintenance on 5 Aaon RTUs. Checked mechanical and electrical components, checked flame sensor readings and temperature rise. Units are heating properly at this time. Quote has been resent to replace RTU 4 belt.
Assisted Kellan Today with full heating maintenance.
Assisted with pm
Performed heating tune up. Signed up for maintenance plan. Declined humidifier tune up.
Performed air conditioning maintenance. Checked all components and safety systems. Checked refrigerant pressures and temperatures for proper heat transfer. Checked system temperature split, for proper cooling inside the home. System is cooling and operational at this time. Spoke to customer about options to improve their indoor air quality. See estimates for details
Thank you for allowing LBA to service your HVAC equipment today. Performed maintenance and safety inspection on the air conditioner. The filter did not need replaced at this time. I washed the outside unit out. I tested all electrical and mechanical components. The refrigerant pressures are within manufacturers specifications at this time. Customer declined enrolling in our P3 Maintenance program *********** *********** *********** *********** *********** *********** *********** **** Please take 60 seconds of your day and leave a review on LBAs Facebook Page and tell the online community about your service with technician Jeremy R.(donâ€™t forget to mention his name) Thank you. *********** *********** *********** *********** *********** *********** *********** ****
Completed full cooling maintenance on 5 RTUs. Checked mechanical and electrical components, washed condenser coils and checked temperature splits. Quotes have been sent for repairs.
Customer complaint that sometimes she have to reset the main breaker when temperature gets about 5 degrees above set point Upon my arrival unit was already in the cooling mode I immediately checked the refrigerant charge and pressure , both are just find, compressor amps name plate is 15.6 the actual amps are 11.3 , condenser motor amps on the name plate is 2.6 the actual amps are 2.0 , I inspected the supply fan belt and checked the supply motor amps, the actual amps are 6.2 and The name plate supply motor amps is 7.5, condenser coil is clean and the filters are ok I cycle the unit off an on about 5 different times still not able to simulate any problems, the best thing to do is next time it shuts off call LBA before the customer reset the breaker if all possible
Performed ac diagnostic. System was low on refrigerant. Performed leak search. Found refrigerant leak at one of the braze joints on the evaporator coil. Repaired leak and recharged system with refrigerant. System is cooling and operational at this time. All repairs completed under an install warranty.
Arrived to do performance maintenance. Inspected the whole air conditioning system to verify operation of all mechanical and electronic components. Verified system charge and temperature split. Upon inspection of the condenser coil found that it was packed with debris and with homeowners approval performed an extensive coil cleaning. Air conditioning system is functioning properly at this time.
I used this work order to renew a maintenance contract. No charge.
4-6-21 tues AC is not working in the SE Nursery at main entry. Spoke to Tracy on site. Found #4 Aaon RTU has a call for cooling Y1,Y2 but the compressor is not running. Found the high-pressure limit wire terminal disconnected The way the wire is configure and the connection, it is very tight and their is no play in the wire. Due to the location on the compressor discharge line. The connection vibrate loose. I cut some of the wire ties to make it a little looser. Also,use electrical tape on both wire connections. System is working at this time, it has a 20Â° evaporator split. Spoke to Tracy about my findings above We checked the air flow in the nursery area. The eastside area compared to the Westside is not getting much airflow. Tracyâ€˜s going to keep an eye on it we may want to get up into the ceiling and check the dampers. RTU #4 Aaon Model #RM-005-8-0-BA01-232 Serial # 200807-AMGE43734
Upon my arrival found thermostat setting for cooling at 67 degrees and heating at 74, I checked the refrigerant charge on the system in heating mode , everything is ok and temperature warm up to set point at 72 degrees, adjusted unit to cooling mode than drop settings down to 67 degrees, unit ran temperature down to 67 degrees before it cycle off , didnâ€™t find much wrong at this time but maybe thermostat settings were off, I set the cooling at 75 degrees and the heating at 70 degrees, being that the pool is heated, the manager Jennifer is not on site but I explained everything to the on-site assistant, again the problem appears to be a thermostat setting problem not an mechanical issue at this time
On unit serial#2016110043 tech will recover remaining refrigerant from system add nitrogen to system for a leak check if able to find the leak tech will explain to customer the cost for repairs, if repairs are made tech will pull a vacuum on system than replace the recovered the refrigerant add additional refrigerant as needed This quote is Only to leak check the system other cost will determine after this procedure is done
Upon arrival I found that the combustion blower had failed, hi inspected system and gave customer estimate to have system fixed as well as offered to get estimate to have it replaced. Customer decided to have system fixed, I replace combustion blower and tested system everything was functioning as it should at this time. Thanks for having me out today, Eli
Customer complaint that dehumidifier is not working Troubleshoot DX AIR model# DVA-097-2-RHN-R-XX-XX serial# 2016110043 and found unit low on refrigerant charge, search for any obvious leaks around the system, didnâ€™t see any leaks, tech recommend and explained to customer that a leak check and repair is needed if leak can be found before adding more refrigerant, I explained to customer (Jennifer) that I will submit a quote for a leak check for starter
Upon arrival I performed a whole house Plumbing inspection. Water pressure was 80 psi within range but at max. I checked natural gas system with a leak detector. No leaks detected.Water heater is a 2012. Home does not have a sump pump. Washing machine hoses showing corrosion recommend replacement. Master bath call handle on lavatory is loose. All other plumbing fixtures operated normally.
No heat call Customer complaint no heat from unit#4 , customer had thermostat turn off , turn thermostat back and set to 71 degrees, troubleshoot at the unit found all safety switches close inspected flame rod and spark igniter, both reading was ok ,taken amp draw on both inducer and supply fan motor, both are reading within tolerance we simulate all the safety switches but didnâ€™t find any problems after cycling the unit off and about 15 times I wasnâ€™t able to any problems at this time , if problems reoccurs might need might need to replace the board
Performed heating checks and changed filters. Found issues of twin system running front lobby area. Quotes have been sent to customer. Goodmanâ€™s Model GKS91155DAXF Serial 1304002745 to have a leaky inducer motor and needs to be replaced. Serial 1304002826 found to have a bad board making the inducer motor run constant which is causing the motor to begin to fail. Recommend replacement of board and inducer assembly. Found Reznor unit thermostat to not be displaying temp properly, recommend thermostat replacement. Two thermostats did have batteries and they were replaced today.
Gathered info and sent to Gregg and Brett for quote.
Unit 1, gas company shut off gas to unit stating it was putting on carbon monoxide and gas into space. Upon further determination found inducer motor not performing correctly which is what might have caused the heat exchanger to get to hot and crack. Unit will not even close pressure switch to attempt to run. Unit (200807-AMGF43728). Recommend replacing all heating elements ( heat exchanger and combustion motor assembly or unit replacement as it is 12 years old and normal life is 15 years of package units. Spoke with Chad and Lisa both are interested in repair and replacement cost and time frame of unit. I have attempted to call Aaon themselves and left a voicemail to get pricing info and a distributor, both I am waiting to here back from on parts pricing and availability. I have been told they are a minimum few weeks out on parts. Commercial replacement form completed and sent for estimating. Customer has been sent a quote for repair, parts will take 2 to 3 weeks to arrive.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
Performed Preventative Maintenance on all RTUS , inspected safety switch, voltage loose wiring, motors amps heat exchanger and operation of heating, everything is working ok at this time
Recommended repairs found during preventative maintenance