Platte City MO Residential HVAC & Plumbing Services
LBA Air Conditioning, Heating & PlumbingRated 4.8 out of 6417 reviews
Your home is your oasis…your own private sanctuary. A place where you can relax knowing that, even if a problem occurs with your plumbing, heating, or air conditioning systems, one quick call to LBA Services will take care of everything. At LBA Air Conditioning, Heating and Plumbing, we work hard, 24/7 if necessary, to give homeowners in Platte City, MO that peace of mind.
Please check out a few of our reviews below to find out why your neighbors consider us to be their go-to heating and air company and local plumber in Platte City, MO.
for Platte City, MO
Our Reviews by City
Main sewer line problems
Jim - Platte City, MO
Great Service, so Friendly~~~
Hillcrest - Platte City, MO
Jim - Platte City, MO
Carly did a great job. He explained everything very well and was very courteous.
Baker - Platte City, MO
Ellen - Platte City, MO
New Garbage Disposal
Tim - Platte City, MO
Great service! Called late on Friday and they had a new disposal by noon on Saturday. I will be calling again!
Pat - Platte City, MO
Ellen B - Platte City, MO
The technician was really nice and took the time to explain any findings and suggestions.
Customer called because smoke/carbon monoxide detector intermittently goes off when she runs a lot of hot water. Unable to recreate smoke alarm going off. Water heater is installed properly. Issue is with smoke alarm installed by another company. Advised customer water heater is not causing problem. Customer will follow up with smoke alarm company to include possibly moving location of alarm or installing doors with bigger venting to allow better air flow into confined utility room in garage. Customer has mild sewer smell when dishwasher and disposal are used. Customer claims 1/2 hp disposal is about 10 years old. Company will remove old disposal and install new 3/4 Hp Pro 750 Installed now 3/4 Hp Pro 750 disposal. 1 year warranty. Thank you for choosing LBA. Have a great day!
Scott to collect after insurance pays customer per scott and customer
No heat Troubleshoot unit and found fuse blown on the unit an a bad inducer motor, customer requested for an immediate repair, parts for the AAON unit are only in Lenexa Kansas, return about two hours later , installed the motor and fuses checked operation of heating mode everything is working ok, customer also asked if I can reattach an thermostat that was falling off the wall I properly secure the thermostat back on the wall AAON Serial#-200807-AMGF43729
Customer stated they are having continued interment issues with Aaon RTU 4 SN:200807-AMGE43734 not heating. When I arrived unit was working properly. I cycled the unit roughly 10 times in order to get it to fail to light. At this point I found the unit was not sending voltage from the direct spark ignition board to the unit safety switches. This board will need to be replaced in order for heat to function. I also closed the fresh air dampers to prevent cold outside air from being brought into the space untill repairs can be made.
Upon arrival I found that the capacitor has failed. I contacted Scott McKinley for pricing and gave customer estimates. Gave customer friends and family discount and he agreed to have system fixed. After repairs were made the system was testing as it should at this time
Completed full heating maintenance on 5 Aaon RTUs. Checked mechanical and electrical components, checked flame sensor readings and temperature rise. Units are heating properly at this time. Quote has been resent to replace RTU 4 belt.
Assisted Kellan Today with full heating maintenance.
Assisted with pm
Performed heating tune up. Signed up for maintenance plan. Declined humidifier tune up.
Performed air conditioning maintenance. Checked all components and safety systems. Checked refrigerant pressures and temperatures for proper heat transfer. Checked system temperature split, for proper cooling inside the home. System is cooling and operational at this time. Spoke to customer about options to improve their indoor air quality. See estimates for details
Thank you for allowing LBA to service your HVAC equipment today. Performed maintenance and safety inspection on the air conditioner. The filter did not need replaced at this time. I washed the outside unit out. I tested all electrical and mechanical components. The refrigerant pressures are within manufacturers specifications at this time. Customer declined enrolling in our P3 Maintenance program *********** *********** *********** *********** *********** *********** *********** **** Please take 60 seconds of your day and leave a review on LBAs Facebook Page and tell the online community about your service with technician Jeremy R.(donâ€™t forget to mention his name) Thank you. *********** *********** *********** *********** *********** *********** *********** ****
Completed full cooling maintenance on 5 RTUs. Checked mechanical and electrical components, washed condenser coils and checked temperature splits. Quotes have been sent for repairs.
Customer complaint that sometimes she have to reset the main breaker when temperature gets about 5 degrees above set point Upon my arrival unit was already in the cooling mode I immediately checked the refrigerant charge and pressure , both are just find, compressor amps name plate is 15.6 the actual amps are 11.3 , condenser motor amps on the name plate is 2.6 the actual amps are 2.0 , I inspected the supply fan belt and checked the supply motor amps, the actual amps are 6.2 and The name plate supply motor amps is 7.5, condenser coil is clean and the filters are ok I cycle the unit off an on about 5 different times still not able to simulate any problems, the best thing to do is next time it shuts off call LBA before the customer reset the breaker if all possible
Performed ac diagnostic. System was low on refrigerant. Performed leak search. Found refrigerant leak at one of the braze joints on the evaporator coil. Repaired leak and recharged system with refrigerant. System is cooling and operational at this time. All repairs completed under an install warranty.
Arrived to do performance maintenance. Inspected the whole air conditioning system to verify operation of all mechanical and electronic components. Verified system charge and temperature split. Upon inspection of the condenser coil found that it was packed with debris and with homeowners approval performed an extensive coil cleaning. Air conditioning system is functioning properly at this time.
I used this work order to renew a maintenance contract. No charge.
4-6-21 tues AC is not working in the SE Nursery at main entry. Spoke to Tracy on site. Found #4 Aaon RTU has a call for cooling Y1,Y2 but the compressor is not running. Found the high-pressure limit wire terminal disconnected The way the wire is configure and the connection, it is very tight and their is no play in the wire. Due to the location on the compressor discharge line. The connection vibrate loose. I cut some of the wire ties to make it a little looser. Also,use electrical tape on both wire connections. System is working at this time, it has a 20Â° evaporator split. Spoke to Tracy about my findings above We checked the air flow in the nursery area. The eastside area compared to the Westside is not getting much airflow. Tracyâ€˜s going to keep an eye on it we may want to get up into the ceiling and check the dampers. RTU #4 Aaon Model #RM-005-8-0-BA01-232 Serial # 200807-AMGE43734
Upon my arrival found thermostat setting for cooling at 67 degrees and heating at 74, I checked the refrigerant charge on the system in heating mode , everything is ok and temperature warm up to set point at 72 degrees, adjusted unit to cooling mode than drop settings down to 67 degrees, unit ran temperature down to 67 degrees before it cycle off , didnâ€™t find much wrong at this time but maybe thermostat settings were off, I set the cooling at 75 degrees and the heating at 70 degrees, being that the pool is heated, the manager Jennifer is not on site but I explained everything to the on-site assistant, again the problem appears to be a thermostat setting problem not an mechanical issue at this time
On unit serial#2016110043 tech will recover remaining refrigerant from system add nitrogen to system for a leak check if able to find the leak tech will explain to customer the cost for repairs, if repairs are made tech will pull a vacuum on system than replace the recovered the refrigerant add additional refrigerant as needed This quote is Only to leak check the system other cost will determine after this procedure is done