Louisburg KS Residential HVAC & Plumbing Services
LBA ServicesRated 4.8 out of 6254 reviews
LBA Services was started by people just like you who want and insist on high quality and reliable service. In Louisburg, KS and throughout the Kansas City area, we treat each family and home as if it were our own. That includes rising to the challenge of being a Hero any time the need calls for extraordinary measures.
From routine maintenance to 24/7 emergency repairs, LBA Services has you covered for all your home plumbing, heating, and air conditioning needs. The same goes for new and replacement system installations. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Louisburg, KS.
for Louisburg, KS
Our Reviews by City
First National - Louisburg, KS
First - Louisburg, KS
First National Bank - Louisburg, KS
We've always had great service but today the technician did not come until 3 pm when we had been told 9am originally and then 11- to 11:30. In neither case were we notified of the delays.
Robert Nauman - Louisburg, KS
Rick is very good. I trust his assessments and advice.
First National Bank of Louisburg - Louisburg, KS
Our technician Rick, does an excellent job of explaining the issues with our systems and then actually performing the repairs. We feel very comfortable with his integrity and skills.
Installed 7.5 ton Rheem outdoor condensing unit. Installed liquid line filter drier, also installed a suction line filter drier.
The compressor for condenser unit two has shorted to ground on all three legs. I was putting together a quote to replace the compressor, the compressor is not available at this time but will be available within a few weeks. The compressor was also a lot more expensive than I thought leaving my quote to replace the compressor approximately the same price it would be to change the whole condenser. Spoke with Bob and he agrees with me that it would be a better use of money to get the new unit and have everything new with a five year warranty. He will be expecting a quote to replace the condenser.
The initial issue was called out for was because the 3A batteries in the thermostat were dead. I changed out the batteries and everything worked how it was supposed to. I was told that the larger carrier condenser (model number 38AUZA08A0A5A0A0A0A0, serial 4414C93961) was loud while operating. I found the split coil to be dirty in the middle. I split the coil and cleaned it out with a hose. This dropped the compressor amp draw from 22.5 down to 18. The compressor has a max run amp rating of 25. The temperature was 78 degrees at my first reading and 82 degrees after I cleaned the unit. The compressor is still a little loud but test within factory guidelines. The evaporator coil temperature was 40 degrees with an indoor temperature of 72 degrees and the condenser coil was 101 with an outdoor ambient temperature of 82.
The 5 ton condenser evaporator fan motor was running but the compressor was not. I hope my gauges up and discovered that the system was out of refrigerant. I was able to find a large leak in the evaporator. Due to age (1993) we will be sending a quote to replace the evaporator and condenser. The furnace is a 2013 Lennox and still in good condition.
Checked the drive thru split system for no cool. Found the blowers running on the twin furnaces with no condenser operation. Found the breaker off to the condenser in the breaker box in the mechanical room. Turned on the breaker and verified operation. Evaporator split was 22-23 degrees after restoring power to the condenser. Customer advised that there was a electrican on site yesterday making repairs. Appears that the breaker was turned off during electrical repairs by mistake.
Checked the building for comfort issues, customer noted that the unit in the drive thru section runs more than the lobby area unit. Verified the operation of both systems in cooling. Checked the supply registers and found the drive thru system serving the north areas of the lobby causing the complaints. Explained the layout of the registers to Bob. Advised without zoning the two systems the issues will continue. Customer will ajust the thermostats to overcome the mixed zones.
10/22/19-Checked the twin gas furnaces for the lobby for no heat. Found the blower motor and control board failed in the right side unit. Found the smart gas valve failed in the left unit. Will pick up parts and return to make the repairs---10/23/19-made repairs to the twin furnaces. Verified operation in heat and cool. Repairs were approved by Bob Nauman.
Lennox heat pump with not shut off
Advised customer on the operations of the heat pump/ air handler and the set points on the thermostat.
Straighten out low voltage wiring at air handler on the add a wire control
$88.00 to us postcard special needs do run capacitor out of range customer wants to wait for now on the repair