Ottawa KS Residential HVAC & Plumbing Services
LBA ServicesRated 4.8 out of 6115 reviews
LBA Services has proudly served the homeowners in Ottawa, KS and the surrounding areas since 1985! Our professional team of local experts is happy to tackle your heating, AC and plumbing problems. From simple maintenance to full replacements, we can help.
We invite you to read some of our reviews below and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Ottawa, KS.
for Ottawa, KS
Our Reviews by City
jones - Ottawa, KS
Representative was on time and completed work as required.
Quoted repairs and emailed Keith Butler the proposal.
I arrived to find the York package unit model ZXG12E4B1AA1A111A2, serial number N1K6997882 with the blower motor and condenser fan motors running. Neither compressor circuit one or two were running. Compressor circuit 1 was disconnected and the condensation drain was dry. The compressor for circuit two was shut off due to high pressure caused by a dirty condenser. I cleaned the condenser and reset the unit. Compressor two came on and ran for third minutes with no issues. Without circuit one the unit is only producing a 14 degree temperature split. Compressor circuit one is completely out of refrigerant. Rick will get with the owner to discuss a repair strategy.
Checked the York rooftop S# N1K6997882 for refrigerant leak in the micro channel condenser. Found the right side compressor unplugged and void of refrigerant. Added nitrogen to locate the leak. Found the leak in the center of the South side of the condenser. Reseached the replacement coil. Called Keith and explained the options for repairs. Sent him a quote for repairs.
Performed pressure test on gas line per city inspector request. Gas line test has been passed at this time bye inspector.
Performed boiler tune up
Full tune up on the Jones Knight boiler and repairs