Bucyrus KS Residential HVAC & Plumbing Services
LBA Air Conditioning, Heating & PlumbingRated 4.8 out of 6892 reviews
LBA Services was started by people just like you who want and insist on high quality and reliable service. In Bucyrus, KS and throughout the Kansas City area, we treat each family and home as if it were our own. That includes rising to the challenge of being a Hero any time the need calls for extraordinary measures.
From routine maintenance to 24/7 emergency repairs, LBA Services has you covered for all your home plumbing, heating, and air conditioning needs. The same goes for new and replacement system installations. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Bucyrus, KS.
for Bucyrus, KS
Our Reviews by City
Awesome service, Good price
Bob - Bucyrus, KS 66013
The technicians were very professional and did a wonderful job installing our new system. They arrived promptly and did great work.
HarkleroadDave - Bucyrus, KS 66013
Alan - Bucyrus, KS 66013
this man was Professional,
William - Bucyrus, KS 66013
Kevin helped me understand my Heating and air. Kevin is the only guy I want at my House. kim and Bill Hickey
carol - Bucyrus, KS 66013
Upon arrival I found that the thermostat was automatically turning to auxiliary heat. Customer also wanted me to check humidifier. I found that the water shut off and solenoid had both failed and gave customer estimates on replacement and repairs. Customer decided to have humidifier replaced and pay using financing. I replaced humidifier and tested all operations. Thanks for having me out today, Eli
Performed blower Clean as well as replaced UV light bulb and humidifier canister. Make sure all three systems ran properly before leaving.
Heating maintenance X3. Checked all task. Checked heat strips. Checked blower motors and wheel upstairs system had biological growth growing on the wheel. Checked humidifiers. Checked outdoor systems. Checked capacitors. Checked refrigerant levels. Checked coils and clean. Recommended replacement of contactor air filter UV light canister to humidifier and blower wheel customer approved. Make sure system room before leaving View visual findings from this job here - https://visionshare.xoi.io/?id=XA-3881-D911A96214BC4F29988D817F1205FB9C
Company arrived Thursday, September 1, 2022. The customer was having issues with their floor drain next to their water heater draining slowly and was interested in replacing the expansion tank to the water heater. Company opened the slow draining floor drain via toilet auger allowing for proper flow. Company gave estimate for the expansion tank replacement and the customer chose to have the work preformed today. Company removed the failed expansion tank and replaced it with new. This will come with a 2 year warranty on parts and labor. Thank you for choosing LBA and have a great day.
Client called because AC wasn't cooling. Ran a diagnostic and found the thermostat was faulty. Replaced the old digital thermostat with a new programmable thermostat. Tested the replacement thermostat and AC began cooling right away.
Return to perform warranty work. System is working as designed at this time.
Warranty Found system not turning off when auxiliary heat come on when thermostat is satisfied with in the heating cycle. Turned thermostat to heat pump only mode system would cycle properly and auxiliary heat will not turn on currently. We will return when Bosch technical support responds with a solution. System was cycling properly in heat pump only mode. We will return when we have a permanent solution. Thank you
Warranty check up Systems auxiliary heat was turning on almost immediately as system turned on. Checked Temperature splits of heat pump was 22â° and with auxiliary was 36â°. Changed setting on thermostat to not turn on auxiliary Heat on design till the Temperature is 10â° (origially 3â° manufacturers specifications) colder than the requested temperature or until the heat pump is running constantly for 15 minutes (originally 10 minutes manufacturers specifications) unless a call for defrost on heat pump is needed. System was not immediately turning on auxiliary heat when call for heat was requested from the thermostat. System operating when technicians left.
Arrived to troubleshoot a noise coming from the air conditioning system. Began investigation at the furnace. Ran air conditioning diagnostic. Found that the blower motor was making excessive noise when the thermostat would satisfy. Verified that the noise was just the blower motor. Ordered the parts and installed a whole new blower assembly. Verified that the system is operational and no longer making excessive noise. Air conditioning system is functioning properly at this time.
08/05/2021 11:35:01 AM - Option 1 <a clicktracking="off" href="https://partsgatorstorage.blob.core.windows.net/proposals/852021 45943 PM - 1 - 13-080521113501-Dave Harkleroad-Proposal-Copy.pdf?sv=2014-02-14&sr=b&sig=PeNIppTowE0G6HLQZ1cGK1FbeTIUGh%2FCDnL8kLkzKzo%3D&st=2021-08-05T18%3A15%3A09Z&se=2521-08-05T18%3A20%3A09Z&sp=rw" target="_blank">View PDF</a>
System has a major refrigerant leak in the a coil and the customer wanted to look into replacement of the heat pump.
Arrived to do performance maintenance. Inspected the air conditioning system to verify operation of all mechanical and electronic components. Verified system charge and temperature split. Changed filter with homeowner supplied filter and cleared condensate line. Air conditioning system is functioning properly at this time.
Customer is applying for financing.
Found floor drain in mechanical room not draining. Turned off water to humidifier. I am going to have a plumber come out in the morning 23 Jan 21.