Peculiar MO Residential HVAC & Plumbing Services
LBA Air Conditioning, Heating & PlumbingRated 4.8 out of 6417 reviews
Your home is your oasis…your own private sanctuary. A place where you can relax knowing that, even if a problem occurs with your plumbing, heating, or air conditioning systems, one quick call to LBA Services will take care of everything. At LBA Air Conditioning, Heating and Plumbing, we work hard, 24/7 if necessary, to give homeowners in Peculiar, MO that peace of mind.
Please check out a few of our reviews below to find out why your neighbors consider us to be their go-to heating and air company and local plumber in Peculiar, MO.
for Peculiar, MO
Our Reviews by City
flemming - Peculiar, MO
Nick has been to our house twice. Once for service and today for winter check up. He is very good and courteous.
Returned to replace high pressure control. Recovered refrigerant, replaced pressure control, pressure tested system with nitrogen at 350psi, pulled vacuum down to 500 microns, charged refrigerant to 18 degrees of subcooling per manufacturers specifications at todayâ€™s outdoor temperature. System is operating within manufacturers specifications.
Found system locked out on a high pressure control fault. Inspected high pressure sensor and found it to have failed. Bypassed high pressure and ran system for over an hour, found refrigerant pressures to be normal and subcooling is at manufacturers required amount. I have ordered a replacement pressure sensor from the factory and we will return to replace once the part arrives at our warehouse.
Returned to install Econet. Installed wall control and wired equipment. Tested equipment and ensured it is properly modulating and going into its highest compressor stage. Everything is working properly at this time.
Modulating heat pump and is doing what it can but is only ramping up to intermediate speed due to not having enough wires and no attic to run a new wire in. We need to return with an eco net so that the system can reach its highest speed.