LaCygne KS Residential HVAC & Plumbing Services
LBA ServicesRated 4.8 out of 6254 reviews
LBA Services has proudly served the homeowners in LaCygne, KS and the surrounding areas since 1985! Our professional team of local experts is happy to tackle your heating, AC and plumbing problems. From simple maintenance to full replacements, we can help.
We invite you to read some of our reviews below and find out why your neighbors consider us to be their nearby heating and air company and local plumber in LaCygne, KS.
for LaCygne, KS
Our Reviews by City
Collected info for adding equipment to the existing PM contract
Performed quoted work Upon arrival I found that Lennox rtu#1 serial # 5607H01292 was off on high head pressure I reset the safety and found that the condenser fan would not come on I checked the capacitor and it checked within tolerance I then checked the windings and found that the fan motor had and internal short to ground. This quote is for all materials and labor it will take to replace the fan motor as well as the fan blade.
Upon arrival I found that they were having issues with units number 1 and 2. While inspecting unit number two I found that the unit test dip switch had not been pushed back to its normal position I switched it back and the unit came on and had a good temperature split. While inspecting unit number one I found that it was off on the high pressure safety I felt the compressor to see if it was hot it was slightly warm so I reset the safety and found that the condenser fan motor was not coming on I tested the capacitor and it was within tolerance, I found that the windings had an internal short to ground. A quote has been sent to the customer to replace the fan motor.
Performed quoted work all units are still operational. Lennox unit # 3 serial # 5607H0121614 was found to have two burnt and pitted 3 pole 24vac 40 amp compressor and blower contactors that I recommend replacing. Lennox unit #4 serial # 5607H01293 was also found with two burnt and pitted 3 pole 24vac 30 amp compressor and blower contactorâ€™s that I recommend replacing. Lennox unit #2 serial # 5607H01293 was found with a burnt and pitted 3 pole 24vac 40 amp compressor contactor that I recommend replacing. This quote includes all parts and labor to replace the contactors.
Performed full cooling preventative maintenance on four rooftop units. Checked all electrical and mechanical components, changed all filters, washed all coils. All units are operational at this time. A quote has been sent to the customer via email for preventative repairs.
Performed full heating preventative maintenance on four rooftop units and two exhaust fans, checked all electrical and mechanical components, changed all filters, all units are working within factory specifications at this time.
Performed the seasonal PM on the four Lennox Rtus and two restroom exhaust fans. Details are in the checkout sheets.
Performed the seasonal pm on the four Rtus and two restroom exhaust fans. See the checkout sheets for details on the findings. Used 8--16x25x2 pleated filters that were picked up at our shop from our stock.